I would like to define a common remote connectivity solution that works across MDL2 and MD4 machines.
Will G3 work on both?
I can open up an MDL2 application file in IQAN Design 5.03, add a G2/G3 modem, connect them both to a diagnostic bus and save the file.
Will IQAN connect work properly ?
Customer support service by UserEcho